Step 1: Disconnect the power supply and the civil electrical system in the installation space.
Step 2: Screw the anti-shock aptomat to the electrical cabinet or electrical panel, with a cover.
When screwing, you should tighten the screw firmly and be careful not to loose during the use of electrical equipment and place the line end at the top, the load end at the bottom.
Step 3: Connect the power cord to the anti-shock aptomat.
When wiring to the anti-shock aptomat, the AC source is attached to the top of the line, the output is attached to the load on the load piles. Should not be mounted in reverse because it will easily cause electric shock and danger to the user.
The hot wire must be connected to the L pile, the cold wire to the N pile. Note, an anti-shock aptomat without overload protection must be installed in series after the MCB and MCCB to ensure the safety of the system when overload occurs. overvoltage.
Step 4: Complete the installation.
After installing the anti-shock aptomat, you should not subjectively use it, but need to check the electrical system to see if the anti-shock aptomat can work to adjust in a timely manner.
*** Note: The product meets the application needs in many different cases with operating temperatures from: -5~40°C.